Main range of productCanalis range compatibilityCanalis KS offer typeComplementary product or component typeTap-off unit busbar trunking compatibilityCanalis KS busbar trunking with plug-in outlets [Ie] rated operational current400 A at 35 °C protection typeCircuit breaker : NSX400 provided equipmentCircuit breaker to be ordered separately mounting modePlug-in with fixed polarity tap-off unit polarity3L+N+PE colourWhite RAL 9001 Complementary device applicationMedium power distribution [Ue] rated operational voltage230...690 V depending on protective device [Uimp] rated impulse withstand voltage6.8 kV [Ui] rated insulation voltage400 V depending on protective device500 V depending on protective device690 V depending on protective device network frequency50/60 Hz control typeMotor mechanism electrical connectionCrimp lug - ISO40 - cable : 50 mm² flexibleCrimp lug - ISO40 - cable : 70 mm² rigid door/cover opening sideRight tap-off unit disconnection modeBy opening the door standardsIEC 61439-1IEC 61439-6 width734.5 mm depth352 mm depth (door open)973.5 mm product weight19 kg Environment earthing systemTTITTN-S IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1751 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsDVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD files for KSB400DB412: TAP OFF UNIT 400A COMPACT NS (Version 1.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.