Main range of productCanalis range compatibilityCanalis KS product or component typeTap-off unit busbar trunking compatibilityCanalis KS busbar trunking with plug-in outlets [Ie] rated operational current32 A protection typeCircuit breaker : miniature circuit breaker (MCB) mounting modePlug-in with fixed polarity tap-off unit polarity3L+N+PE colourWhite RAL 9001 Complementary device applicationMedium power distribution provided equipmentBlanking plateCircuit breaker to be ordered separately [Ue] rated operational voltage230...690 V depending on protective device [Uimp] rated impulse withstand voltage6.8 kV [Ui] rated insulation voltage400 V depending on protective device500 V depending on protective device690 V depending on protective device network frequency50/60 Hz electrical connectionPre-wired terminal block - ISO32 - cable : 6 mm² flexiblePre-wired terminal block - ISO32 - cable : 10 mm² rigid door/cover opening sideFront tap-off unit disconnection modeBy drawing out standardsIEC 61439-1IEC 61439-6 18 mm pitches5 width135 mm depth108 mm height175 mm product weight0.6 kg Environment earthing systemTTITTN-S IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1012 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for KSB32CM55: Canalis - KSB - Connector - For 5 modular devices - 32A (Version 2.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.