Main range of productCanalis range compatibilityCanalis KS product or component typeTap-off unit busbar trunking compatibilityCanalis KS busbar trunking with plug-in outlets [Ie] rated operational current160 A protection typeCircuit breaker : miniature circuit breaker (MCB) mounting modePlug-in with fixed polarity tap-off unit polarity3L+PEN colourWhite RAL 9001 Complementary device applicationMedium power distribution provided equipmentBlanking plateCircuit breaker to be ordered separatelyDIN rail (x4) [Ue] rated operational voltage230...690 V depending on protective device [Uimp] rated impulse withstand voltage6.8 kV [Ui] rated insulation voltage400 V depending on protective device500 V depending on protective device690 V depending on protective device network frequency50/60 Hz electrical connectionLugs - ISO50 - cable : 35 mm² flexibleLugs - ISO50 - cable : 50 mm² rigid door/cover opening sideDown tap-off unit disconnection modeBy drawing out standardsIEC 61439-1IEC 61439-6 body materialMetal 18 mm pitches24 width494 mm depth308 mm depth (door open)650 mm height303 mm product weight10.69 kg Environment earthing systemTN-C IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1751 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsCanalis - KSB - Tap-off unit - 160A (Version 1.0)DVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD files for KSB160SM524: TAP OFF UNIT 160A 24 MODULES (Version 1.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.