Main range of productCanalis range compatibilityCanalis KTCanalis KS product or component typeTap-off unit busbar trunking compatibilityCanalis KS busbar trunking with plug-in outletsCanalis KT busbar trunking with KS type plug-in outlets [Ie] rated operational current100 A protection typeCircuit breaker : miniature circuit breaker (MCB) mounting modePlug-in with fixed polarity tap-off unit polarity3L+PEN colourWhite RAL 9001 Complementary device applicationMedium power distribution provided equipmentCircuit breaker to be ordered separately [Ue] rated operational voltage230...690 V depending on protective device [Uimp] rated impulse withstand voltage6.8 kV [Ui] rated insulation voltage400 V depending on protective device500 V depending on protective device690 V depending on protective device network frequency50/60 Hz electrical connectionLugs - ISO63 - cable : 35 mm² flexibleLugs - ISO63 - cable : 35 mm² rigid door/cover opening sideRight tap-off unit disconnection modeBy opening the door standardsIEC 61439-1IEC 61439-6 18 mm pitches12 width444 mm depth133 mm depth (door open)545.5 mm height220 mm product weight5 kg Environment earthing systemTN-C IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1012 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD files for KSB100SM512: TAP-OFF UNIT 100 A 12 MODULES (Version 1.0)DVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)Canalis - KSB - Tap-off unit - 100A (Version 1.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.