Main range of productCanalis range compatibilityKN busbar trunking product or component typeTap-off unit busbar trunking compatibilityCanalis KN busbar trunkingplug-in [Ie] rated operational current50 A at 35 °C protection typefuse isolator: Neozed fuse, size E18 conforming to DIN provided equipmentfuse to be ordered separately mounting modePlug-in with fixed polarity tap-off unit polarity3L+N+PE3L+PE colourWhite (RAL 9001) Complementary device applicationLow power distribution [Ue] rated operational voltage230...500 V depending on protective device [Uimp] rated impulse withstand voltage4.6 kV [Ui] rated insulation voltage500 V depending on protective device network frequency50/60 Hz electrical connectionCable clamp terminal - ISO50 16 mm² flexibleCable clamp terminal - ISO50 16 mm² rigid door/cover opening sideRight tap-off unit disconnection modeBy opening the door standardsIEC 61439-1IEC 61439-6 width344 mm depth101 mm depth (door open)432.5 mm height165 mm net weight1.5 kg Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveUnder investigation Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsCAD file (on TraceParts) for KNB50SN4: Canalis - tap-off unit with isolator for DIN fuse, Neozed size E18 - 50A 3L+N+PE (Version 2.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.