Main rangeEVlink product nameEVlink parking product or component typeCharging station device short nameEVW2 poles description1P + N for control circuit1P + N for power circuit mounting modeWall-mounted offer typeStandard rated supply voltage230 V AC 50/60 Hz power circuit220...240 V AC 50/60 Hz control circuit earthing systemITTTTN socket-outlet number1 socket-outlet typeRight side : T2 with shutter / silver plated contacts supply current32 A for T2 with shutter Max power7 kW for T2 with shutter Complementary control type1 red push-button function : stop1 green illuminated push-button function : start/unlock flap local signalling1 green LED flashing on side device function: on charge1 green LED on front device function: available1 orange LED on front device function: reserved1 red LED on front device function: not operational communication port protocolOCPP 1.6 Configuration /ArchitectureStandaloneClustured architecture Operation and maintenanceUser privilege configurationCharge detail recordsPostponed chargeCircuit breaker statusLoad managementDiagnosis capabilities web serverEmbedded Ethernet serviceConfiguration via web server standardsIEC 61851-22IEC 61851-1 product certificationsCBCEEV ReadyZE Ready height620 mm width413 mm depth256 mm product weight33 kg colourWhite RAL 9003 on front deviceGrey RAL 7016 on side device Environment IP degree of protectionIP54 off load conforming to IEC 61851-1IP54 on load conforming to IEC 61851-1 IK degree of protectionIK10 charging station conforming to IEC 61851-22IK10 socket-outlet conforming to IEC 61851-22 ambient air temperature for operation-30...50 °C conforming to IEC 61851-22 ambient air temperature for storage-40...80 °C operating altitude0...2000 m conforming to IEC 61851-22 relative humidity0...95 % Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions
Documents and DownloadsLanguage
Instruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.