Main rangeEVlink product nameEVlink parking product or component typeEnclosure device short nameEVP2 range compatibilityEVlink parking EVF2 charging stationEVlink parking EVW2 charging station poles description3P + N for power circuit1P + N for control circuit mounting modeWall-mountedFloor-standing offer typeStandard rated supply voltage230 V AC 50/60 Hz control circuit380...415 V AC 50/60 Hz power circuit earthing systemITTNTT socket-outlet number2 socket-outlet typeLeft side: T2 with shutter / silver plated contactsRight side: TE / silver plated contacts maximum supply current32 A for T2 with shutter10 A for TE Max power22 kW for T2 with shutter2.3 kW for TE Complementary control type2 red push-button, function: stop2 green illuminated push-button, function: start/unlock flap local signallingOn charge: 2 LED (green) (flashing) on sideAvailable: 2 LED (green) on frontReserved: 2 LED (orange) on frontNot operational: 2 LED (red) on front web serverEmbedded Ethernet serviceConfiguration via web server height625 mm width400 mm depth206 mm net weight20 kg colourGrey (RAL 7016) Environment IP degree of protectionIP54 off load conforming to IEC 61851-1IP54 on load conforming to IEC 61851-1 IK degree of protectionIK10 charging station conforming to IEC 61851-22IK10 socket-outlet: T2 with shutter conforming to IEC 61851-22IK08 socket-outlet: TF ambient air temperature for operation-25…40 °C conforming to IEC 61851-22 ambient air temperature for storage-40…80 °C operating altitude0...2000 m conforming to IEC 61851-22 relative humidity0…95 % Offer Sustainability REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Instruction sheetFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.