Main range of productAccuSine product nameAccuSine PFV+ product or component typeElectronic VAR controller Complementary Network type3P Network configuration3 or 4 wires network rated voltage208…240 V AC network frequency50/60 Hz +/- 3 % auto-sensing maximum permissible voltage1.1 x Un RMS output current rating60 A reactive power rating25 kvar 240 V AC 50/60 Hz operating modePower factor correctionMains current balancingVolt-var support Installation locationIndoor enclosure mountingFloor-standing protection typeCircuit breaker protection Disconnect typeDoor-interlocked with rotary handle Interrupt capacity200 kA Heat dissipationRear plenum with forced ventilation for high heat flow electromagnetic compatibilityConducted EMC, class A conforming to EN 61000-6-4 accessibility for operationFront location of connectionTop or bottom Environment Enclosure degree of protectionIP31 environmental characteristicOperating: 3C2 conforming to IEC 60721-3-3Operating: 3S2 conforming to IEC 60721-3-3Storage: 3C3 conforming to IEC 60721-3-3Storage: 3S3 conforming to IEC 60721-3-3 operating altitude<= 1000 m 1 % per 100 m ambient air temperature for operation0…40 °C0…50 °C maximum with current derating of 2 % per °C relative humidity0…95 % PCBA protectionConformal coated standardsCSA C22.2 No 60947-1-07EN 61000-6-4UL 508UL 60947-1EN 60439-1CSA C22.2 No 14 product certificationsRCMCULusCEABS ambient air temperature for storage-20…60 °C net weight234 kg height2100 mm width800 mm depth500 mm colourLight grey (RAL 7035) Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
User guideSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.