Main rangeTeSys product nameTeSys DPER product or component typeThermal overload relay device short nameDPER device applicationProtection relay applicationMotor protection phase failure sensitivityTripping current I 30 % of Ir on one phase, the others at Ir conforming to IEC 60947-4-1 quantity per setSet of 1 Complementary network typeAC network frequency50/60 Hz mounting supportScrew clamp tripping threshold1.14 +/-0.06 In A conforming to IEC 60947-4-1 surge withstand6 kV conforming to IEC 60801-5 protection typeBS fuse of 5 A in control circuitGB2 circuit breaker of 5 A in control circuitGG fuse of 5 A in control circuit [Ui] rated insulation voltage690 V AC conforming to IEC 60947-4-1600 V AC conforming to CSA connections - terminalsScrew clamp terminals control circuit 2 1...2.5 mm² flexible withoutScrew clamp terminals control circuit 2 1...2.5 mm² flexible withScrew clamp terminals control circuit 2 1...2.5 mm² solid withoutScrew clamp terminals control circuit 1 1...2.5 mm² flexible withScrew clamp terminals control circuit 1 1...2.5 mm² flexible without tightening torque1.7 N.m of control circuit with screw clamp terminals height137 mm width45 mm depth70 mm product weight0.124 kg Environment standardsIEC 60947-1IEC 60947-4-1EN 60947-4-1 product certificationsCCCULCSA protective treatmentTH conforming to IEC 60068-2-52TH conforming to IEC 60068-2-30 IP degree of protectionIP2x conforming to VDE 0106 ambient air temperature for operation-20...60 °C conforming to IEC 60947-4-1 shock resistance15 gn, duration : 11 ms conforming to IEC 60068-2-7 dielectric strength6 kV at 50 Hz conforming to IEC 60255-5 vibration resistance6 gn on plate conforming to IEC 60068-2-6 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsAvailable
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.