TeSyS fuse-disconnector 1P N 50A - fuse size 14 x 51 mm - blown fuse indicatorShow more characteristics >
Add to My Products Remove from My Products
Main rangeTeSys product nameTeSys DF product or component typeFuse-disconnector device short nameDF14 poles description1P + N Complementary mounting supportRail mounting positionVertical +/- 23° control typeToggle [Ie] rated operational current50 A for power circuit [Uimp] rated impulse withstand voltage8 kV fire resistance960 °C conforming to IEC 60695-2-1 [Ipk] rated peak withstand current15 kA with tubular links conforming to IEC 60269-1 short-circuit withstand120 kA 400 V conforming to IEC 60947-3120 kA 500 V conforming to IEC 60947-380 kA 690 V conforming to IEC 60947-3 local signallingBlown fuse indication fuse size14 x 51 mm fuse typeAMGG [Ui] rated insulation voltage690 V for power circuit AC690 V for power circuit DC connections - terminals1 solid cable(s) 2.5...25 mm² on screw clamp terminals for power circuit2 solid cable(s) 2.5...10 mm² on screw clamp terminals for power circuit1 flexible cable(s) 2.5...25 mm² without cable end on screw clamp terminals for power circuit2 flexible cable(s) 2.5...10 mm² without cable end on screw clamp terminals for power circuit1 flexible cable(s) 2.5...25 mm² with cable end on screw clamp terminals for power circuit2 flexible cable(s) 2.5...10 mm² with cable end on screw clamp terminals for power circuit tightening torque3.5 N.m power circuit : on screw clamp terminals quantity per setSet of 3 Environment standardsIEC 60947-3UL 512CSA C22.2 No 39 product certificationsUR IP degree of protectionIP20 conforming to IEC 60529 protective treatmentTH ambient air temperature for storage-40...80 °C ambient air temperature for operation-20...60 °C with derating height110.8 mm width52.5 mm depth76.5 mm product weight0.293 kg Offer Sustainability RoHS (date code: YYWW) REACh Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.