Main range of productActi 9 product nameActi 9 SCU product or component typeRemote control dimmer device short nameSCU Complementary device applicationBuilding load type<= 50 fluocompact lamp, ballast : electronic, ( <= 1500 W )12 dual mounted fluorescent tube, ballast : electronic, ( 58 W )20 dual mounted fluorescent tube, ballast : electronic, ( 36 W )25 fluorescent tube, ballast : electronic, ( 58 W )40 dual mounted fluorescent tube, ballast : electronic, ( 18 W )40 fluorescent tube, ballast : electronic, ( 36 W )50 fluorescent tube, ballast : electronic, ( 18 W ) control typeLocal control : push-buttonRemote control : push-button power consumption in VA0.8 VA thermal losses3 W input type4 push-button : allows control up to 20 dimmers [Ue] rated operational voltage230 V ( +/- 10 % ) AC, 50 Hz input voltage12...30 V AC/DC output current0.2...100 mA protection typeElectronic overvoltage protectionSingle shot thermal fuseElectronic overload protectionElectronic over temperature protection mounting supportDIN rail 9 mm pitches8 connected auxiliariesMaximum 25 auxiliary push-buttons without light indication, distance : < 50 mMaximum 5 auxiliary push-buttons with light indication, distance : < 50 m connections - terminalsScrew terminals, 2 cable(s) <= 4 mm² topScrew terminals, 5 cable(s) <= 2.5 mm² bottom cable distance between devices50 m height85 mm width72 mm depth62 mm product weight130 g Environment IP degree of protectionIP20 standardsEN 60669-2-1 directives73/23/EEC - low voltage directive89/336/EEC - electromagnetic compatibility ambient air temperature for operation0...70 °C ambient air temperature for storage0...60 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
User guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsApplication solutionsSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.