Main range of productActi 9 product nameActi 9 STD product or component typeRemote control dimmer device short nameSTD Complementary device applicationBuilding load typeHalogen lamp, ( 230 V ) ( AC ) ( 60...1000 W )Incandescent lamp, ( 230 V ) ( AC ) ( 60...1000 W )Low voltage halogen lamp with conventional transformer, ( 60...1000 W )Motor, ( 60...600 W ) control typeLocal control : push-buttonRemote control : push-button power consumption in VA0.8 VA thermal losses3 W input type4 push-button : allows control up to 20 dimmers [Ue] rated operational voltage230 V ( +/- 10 % ) AC, 50 Hz input voltage12...30 V AC/DC protection typeElectronic overload protectionElectronic over temperature protectionSingle shot thermal fuseElectronic overvoltage protection mounting supportDIN rail 9 mm pitches8 connected auxiliariesMaximum 25 auxiliary push-buttons without light indication, distance : < 50 mMaximum 5 auxiliary push-buttons with light indication, distance : < 50 m connections - terminalsScrew terminals, 2 cable(s) <= 4 mm² topScrew terminals, 5 cable(s) <= 2.5 mm² bottom cable distance between devices50 m height85 mm width72 mm depth62 mm product weight130 g Environment IP degree of protectionIP20 standardsEN 60669-2-1 directives73/23/EEC - low voltage directive89/336/EEC - electromagnetic compatibility ambient air temperature for operation0...70 °C ambient air temperature for storage0...60 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1426 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
User guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsCatalogue pageSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.