No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Right and Front Views(1)+ 200 mm / 7.87 in. with option enclosure plinth or increased protection degree IP54(2)+ 400 mm / 15.74 in. with option connection enclosure cable from top/bottom
Mounting and ClearanceMounting and Clearance(1)Air inflow temperature: -10...+50 °C (below 0 °C with option enclosure heating, above +40 °C with derating).
Connections and SchemaTypical Wiring Diagram of the Frequency InverterF1External pre-fuse or circuit breakerMSBuilt-in main switchT01Control transformer 400 / 230 V ACMFaR fusesRFIBuilt-in RFI filterLCLine reactor chokeRECRectifier moduleINVInverter moduleFCdv/dt filter (from 355 kW the dv/dt filter choke 150 m is built-in as standard)CTRLControl panelA01Control terminals at the control blockX200 / X205Control terminals at the control panel (depending on the chosen options)M11Fan in enclosure door(1)Relay control(2)Reference valueStructure of the Control Block(1)Digital inputs(2)Analog inputs(3)Relay outputs(4)STO (Safe Torque Off) and analog outputs(5)RJ45 port for door mounting kit of the graphic keypad(6)RJ45 port for Ethernet IP or Modbus TCP(7)Sink-Ext-Source selector switch (see switch configuration below)(8)RJ45 port for serial Modbus(9)Slot for I/O expansion card(10)Slot for fieldbus or I/O expansion cardControl Block Wiring Diagram(1)Safe Torque Off(2)Analog Output(3)Digital Input(4)Reference potentiometer(5)Analog InputR1A, R1B, R1C :Fault relayR2A, R2C :Sequence relayR3A, R3C :Sequence relaySensor Connection
It is possible to connect either 1 or 3 sensors on terminals AI2 or AI3.Sink / Source Switch Configuration
The switch is used to adapt the operation of the logic inputs to the technology of the programmable controller outputs.
Switch Set to SRC (Source) Position Using the Output Power Supply for the Digital InputsSwitch Set to SRC (Source) Position and Use of an External Power Supply for the DIsSwitch Set to SK (Sink) Position Using the Output Power Supply for the Digital InputsSwitch Set to EXT Position Using an External Power Supply for the DIs
Set the switch to Source (factory setting) if using PLC outputs with PNP transistors.
Set the switch to Ext if using PLC outputs with NPN transistors.
Performance CurvesDerating CurvesNormal DutyIn :Nominal Drive CurrentSF :Switching FrequencyHeavy DutyIn :Nominal Drive CurrentSF :Switching Frequency