Acti 9 iID - RCCB - 4P - 100A - 30mA - type A-GShow more characteristics >
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeActi 9 product nameActi 9 iID product or component typeResidual current circuit breaker (RCCB) device short nameIID poles description4P neutral positionLeft [In] rated current100 A network typeAC earth-leakage sensitivity30 mA earth-leakage protection time delayDelayed earth-leakage protection classType A-G Complementary network frequency50/60 Hz [Ue] rated operational voltage380...415 V AC 50/60 Hz rated breaking and making capacityIm 1500 AIdm 1500 A rated conditional short-circuit current10 kA [Ui] rated insulation voltage500 V AC 50/60 Hz [Uimp] rated impulse withstand voltage6 kV contact position indicatorYes control typeToggle mounting modeClip-on mounting supportDIN rail 9 mm pitches8 height91 mm width72 mm depth73 mm product weight0.37 kg colourWhite mechanical durability20000 cycles electrical durability10000 cycles AC-1 locking options descriptionPadlocking device connections - terminalsDouble terminal, front rigid wire(s) 1...35 mm² maxDouble terminal, front flexible wire(s) 1...25 mm² maxDouble terminal, front flexible with ferrule wire(s) 1...25 mm² maxDouble terminal, back rigid wire(s) 1...25 mm² maxDouble terminal, back flexible wire(s) 1...16 mm² maxDouble terminal, back flexible with ferrule wire(s) 1...16 mm² max wire stripping length14 mm (top or bottom) tightening torque3.5 N.m (top or bottom) Environment standardsEN/IEC 61008-1 IP degree of protectionIP40 for modular enclosure conforming to IEC 60529IP20 conforming to IEC 60529 pollution degree3 electromagnetic compatibility8/20 µs impulse withstand, 250 A conforming to EN/IEC 61008-1 ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Contractual warranty Warranty period18 months
Documents and DownloadsCADSizeAdd to My DocumentsActi9 iID 4P 25A…100A; Double terminal Residual Current Circuit Breaker (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.