Main rangeActi 9 product nameActi 9 iSW product or component typeSwitch disconnector device short nameISW device applicationControl poles description4P utilisation categoryAC-22A suitability for isolationYes Complementary [Ie] rated operational current20 A at 415 V AC 50/60 Hz [Ue] rated operational voltage415 V AC 50/60 Hz [Ui] rated insulation voltage500 V AC 50/60 Hz conforming to EN/IEC 60669-2-4 [Uimp] rated impulse withstand voltage4 kV control typeToggle local signallingON/OFF indication contact position indicatorYes mounting modeFixed mounting supportDIN rail 9 mm pitches4 height77 mm width36 mm depth70 mm colourWhite mechanical durability300000 cycles electrical durability30000 cycles connections - terminalsTunnel type terminals - 10 mm² - rigidTunnel type terminals - 10 mm² - flexibleTunnel type terminals - 10 mm² - flexible with ferrule wire stripping length9 mm tightening torque1.2 N.m Environment standardsEN/IEC 60669-2-4 IP degree of protectionIP4 pollution degree2 tropicalisation2 relative humidity95 % at 55 °C ambient air temperature for operation-20…50 °C ambient air temperature for storage-40…70 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveUnder investigation Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsCertificate iSW 20-32A according to EN 60669-1 and EN 60669-2-4 (Version 1.0)Declaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.