Main rangeProdis product or component typeAdd-on residual current devices device short nameVigi TG40 poles description1P + N neutral positionLeft [In] rated current25 A network typeAC earth-leakage sensitivity300 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType AC Complementary device location in systemGroup incomer network frequency50 Hz [Ue] rated operational voltage230 V AC 50 Hz phase to neutral residual current tripping technologyVoltage independent [Ui] rated insulation voltage400 V AC 50 Hz conforming to EN 61009-1 [Uimp] rated impulse withstand voltage6 kV conforming to EN 61009-1 local signallingON/OFF indication mounting modeClip-on mounting supportDIN rail electrical connection to mcbBy screws 9 mm pitches2 height82 mm width18 mm depth70 mm product weight90 g colourWhite connections - terminalsCable, upstream rigid wire(s) 0.75...16 mm² maxCable, upstream flexible wire(s) 0.33...10 mm² max wire stripping length13 mm tightening torque2 N.m Environment standardsIEC 60947-2EN 61009-1EN 61009-2-1 IP degree of protectionIP20 conforming to IEC 60529 pollution degree3 conforming to EN 61009-1 tropicalisation2 conforming to IEC 60068-1 relative humidity95 % ( 55 °C ) operating altitude2000 m ambient air temperature for operation-5...60 °C ambient air temperature for storage-40...60 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1201 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCAD file (on TraceParts) for A9N21481: ProDis - earth leakage add-on block - Vigi TG40 - 1P + N - 25A - 300mA (Version 2.0)Product Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.