Main product or component typeAdd-on residual current devices device short nameVigi C120 poles description4P [In] rated current125 A network typeAC earth-leakage sensitivity30 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType A-SI Complementary device location in systemOutgoer network frequency50 Hz [Ue] rated operational voltage230...415 V AC 50 Hz residual current tripping technologyVoltage independent [Ui] rated insulation voltage500 V AC 50/60 Hz conforming to IEC 60947-1 [Uimp] rated impulse withstand voltage6 kV conforming to IEC 60947-2 mounting modeClip-on mounting support35 mm symmetrical DIN rail electrical connection to mcbBy screws 9 mm pitches10 height95 mm width198 mm depth73 mm net weight0.58 kg colourWhite mechanical durability20000 cycles connections - terminalsTunnel type terminals1…35 mm² flexibleTunnel type terminals1…50 mm² rigid wire stripping length15 mm tightening torque3.5 N.m Environment standardsEN 61009 IP degree of protectionIP20 pollution degree3 conforming to IEC 60947-2 ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…60 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveUnder investigation Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CADSizeAdd to My DocumentsVigi C120 125A 4P 30m...1000mA; Adaptable residual current device Acti 9 (Version 1.0)Vigi C120 125A 4P 30mA…1000mA; Adaptable residual current device (Version 1.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.