Main product or component typeAdd-on residual current devices device short nameVigi C120 poles description2P [In] rated current125 A network typeAC earth-leakage sensitivity300 mA earth-leakage protection time delaySelective earth-leakage protection classType AC Complementary device location in systemOutgoer network frequency50/60 Hz [Ue] rated operational voltage230...415 V AC 50/60 Hz residual current tripping technologyVoltage independent [Ui] rated insulation voltage500 V AC 50/60 Hz conforming to IEC 60947-1 [Uimp] rated impulse withstand voltage6 kV conforming to IEC 60947-2 mounting modeClip-on mounting support35 mm symmetrical DIN rail electrical connection to mcbBy screws 9 mm pitches7 height95 mm width117 mm depth73 mm product weight0.325 kg colourWhite mechanical durability20000 cycles connections - terminalsTunnel type terminals rigid wire(s) 1...50 mm² maxTunnel type terminals flexible wire(s) 1...35 mm² max wire stripping length15 mm tightening torque3.5 N.m Environment standardsEN 61009 IP degree of protectionIP20 pollution degree3 conforming to IEC 60947-2 ambient air temperature for operation-5...60 °C ambient air temperature for storage-40...60 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW)Compliant - since 1201 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
CADSizeAdd to My DocumentsVigi C120 125A 2P 30mA…1000mA; Adaptable residual current device (Version 1.0)Vigi C120 125A 2P 30mA…1000mA; Adaptable residual current device (Version 1.0)Vigi C120 125A 2P 30m...1000mA; Adaptable residual current device Acti 9 (Version 1.0)CertificateSizeAdd to My DocumentsCertificate VIGI C120 according to IEC 61009-1 and IEC 61009-2-1 (Version 1.0)Instruction sheetSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.