A9L16673 is replaced by:
Main range of productActi 9 product nameActi 9 iPRD product or component typeSurge arrester with pluggable cartridge device short nameIPRD20 device applicationDistribution poles description4P remote signallingWithout surge arrester typeElectrical distribution network earthing systemTN-C Complementary surge arrester class typeType 2 surge arrester technologyMOV [Ue] rated operational voltage230 V (+/- 10 %) AC 50/60 Hz400 V (+/- 10 %) AC 50/60 Hz [In] nominal discharge currentCommon mode : 5 kA L/PECommon mode : 5 kA N/PE [Imax] maximum discharge currentCommon mode : 20 kA L/PECommon mode : 20 kA N/PE [Uc] maximum continuous operating voltageCommon mode : 340 V L/PECommon mode : 340 V N/PE [Up] voltage protection level<= 1.1 kV type 2 common mode L/PE<= 1.1 kV type 2 common mode N/PE [I total] discharge current80 kA disconnector device typeAssociated circuit breaker iC60N 25 A curve C - Icu 10 kAAssociated circuit breaker iC60H 25 A curve C - Icu 15 kAAssociated circuit breaker iC60L 25 A curve C - Icu 25 kA mounting modeClip-on mounting supportDIN rail 9 mm pitches8 height81 mm width72 mm depth69 mm colourWhite ( RAL 9003 ) response time<= 25 ns connections - terminalsTunnel type terminal, downside 2.5...35 mm²Tunnel type terminal, upside 2.5...35 mm² tightening torque2.5 N.m Environment standardsEN 61643-11IEC 61643-11 product certificationsCE quality labelsKEMA-KEURNFOVE IP degree of protectionOn front face : IP40 conforming to IEC 60529Built-in : IP20 conforming to IEC 60529 IK degree of protectionIK03 conforming to IEC 62262 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months 18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.