A9L16567 is replaced by:
Main range of productActi 9 product nameActi 9 iPRD product or component typeSurge arrester with pluggable cartridge device short nameIPRD device applicationDistribution poles description1P + N remote signallingWithout surge arrester typeElectrical distribution network earthing systemTN-STT Complementary surge arrester class typeType 2 surge arrester technologyMOV + GDT [Ue] rated operational voltage230 V (+/- 10 %) AC 50/60 Hz [In] nominal discharge currentCommon mode : 15 kA L/PECommon mode : 15 kA N/PEDifferential mode : 15 kA L/N [Imax] maximum discharge currentCommon mode : 40 kA L/PECommon mode : 40 kA N/PEDifferential mode : 40 kA L/N [Uc] maximum continuous operating voltageCommon mode : 260 V N/PECommon mode : 340 V L/PEDifferential mode : 340 V L/N [Up] voltage protection level<= 1.4 kV type 2 common mode N/PE<= 1.4 kV type 2 differential mode L/N disconnector device typeAssociated circuit breaker iC60N 40 A curve C - Icu 10 kAAssociated circuit breaker iC60H 40 A curve C - Icu 15 kAAssociated circuit breaker iC60L 40 A curve C - Icu 25 kA mounting modeClip-on mounting supportDIN rail 9 mm pitches4 height81 mm width36 mm depth69 mm colourWhite ( RAL 9003 ) response time<= 25 ns connections - terminalsTunnel type terminal, downside 2.5...35 mm²Tunnel type terminal, upside 2.5...35 mm² tightening torque2.5 N.m Environment standardsEN 61643-11IEC 61643-11 product certificationsCE quality labelsKEMA-KEURNFOVE IP degree of protectionOn front face : IP40 conforming to IEC 60529Built-in : IP20 conforming to IEC 60529 IK degree of protectionIK03 conforming to IEC 62262 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months 18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.