Main range of productActi 9 product nameActi 9 iPRC device short nameIPRC product or component typeSurge arrester number of protected lines2 surge arrester typeTelecom protection Complementary remote signallingWithout surge arrester technologyGDT + diode [In] rated current0.45 A (up to 45 °C) [Ue] rated operational voltage130 V AC nominal discharge currentCommon mode : 10 kA L/PEDifferential mode : 10 kA L/N [Uc] maximum continuous operating voltageDifferential mode : 185 V DC L/NCommon mode : 130 V AC L/PEDifferential mode : 130 V AC L/NCommon mode : 185 V DC L/PE [Up] voltage protection level<= 160 V type 2 differential mode L/N<= 200 V type 2 common mode L/PE output voltage limitsCommon mode : < 300 V at 1 kV/µsDifferential mode : < 300 V at 1 kV/µs [I total] discharge current10 kA mounting modeFixed mounting support35 mm symmetrical DIN rail 9 mm pitches2 height90 mm width18 mm depth66 mm product weight25 g colourWhite materialPA6 response time< 500 ns connections - terminalsScrew clamp terminal 0.2...4 mm² rigidScrew clamp terminal 0.2...2.5 mm² flexibleScrew clamp terminal 0.2...2.5 mm² flexible with ferrule wire stripping length8 mm tightening torque0.8 N.m Environment standardsEN 61643-21IEC 61643-21 product certificationsXDSL compliance IP degree of protectionIP40 ( in modular enclosure) conforming to IEC 60529IP20 conforming to IEC 60529 IK degree of protectionIK05 conforming to IEC 62262 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Offer Sustainability RoHS (date code: YYWW)Compliant - since 1312 - Schneider Electric declaration of conformity
Schneider Electric declaration of conformity
REACh Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsiPRC for Telecom network surge Arrester (Version 1.0)iPRC for Telecom network surge Arrester (Version 1.0)
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.