Main range of productActi 9 product nameActi 9 iPF product or component typeSurge arrester device short nameIPF8 device applicationDistribution poles description1P remote signallingWithout surge arrester typeElectrical distribution network earthing systemTN-CTT [Uoc] open circuit voltage10 kV type 3 common mode L/PE Complementary surge arrester class typeType 2 + 3 surge arrester technologyMOV [Ue] rated operational voltage230 V (+/- 10 %) AC 50/60 Hz [In] nominal discharge currentCommon mode : 2.5 kA L/PECommon mode : 2.5 kA N/PE [Imax] maximum discharge currentCommon mode : 8 kA L/PE [Uc] maximum continuous operating voltageCommon mode : 340 V L/PECommon mode : 340 V N/PE [Up] voltage protection level<= 1 kV type 2 common mode L/PE<= 1 kV type 2 differential mode L/N<= 1.1 kV type 3 differential mode L/N<= 1.1 kV type 3 common mode L/PE disconnector device typeAssociated circuit breaker iC60H 20 A curve C - Icu 15 kAAssociated circuit breaker iC60N 20 A curve C - Icu 10 kAAssociated circuit breaker iC60L 20 A curve C - Icu 25 kA mounting modeClip-on mounting supportDIN rail 9 mm pitches2 height80.8 mm width17.7 mm depth69 mm product weight0.098 kg colourWhite ( RAL 9003 ) response time<= 25 ns connections - terminalsTunnel type terminal, downside 2.5...35 mm²Tunnel type terminal, upside 2.5...35 mm² tightening torque2.5 N.m Environment standardsEN 61643-11IEC 61643-11 product certificationsCE quality labelsNFKEMA-KEUROVE IP degree of protectionOn front face : IP40 conforming to IEC 60529On terminal : IP20 conforming to IEC 60529 IK degree of protectionIK03 conforming to IEC 62262 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Offer Sustainability RoHS (date code: YYWW) REACh Contractual warranty Warranty period18 months 18 months
Documents and DownloadsLanguage
Instruction sheetSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.