Main range of productActi 9 product nameActi 9 iCT+ product or component typeContactor device short nameICT+ device applicationControl circuit Poles1P [Ie] rated operational current20 A AC-7A20 A AC-7B pole contact composition1 NO network typeAC control typeRemote control [Uc] control circuit voltage230 V AC 50 Hz Complementary network frequency50 Hz [Ue] rated operational voltage250 V AC 50 Hz maximum power3.6 kW 250 V AC [Ui] rated insulation voltage300 V control signal typeMaintained switching frequency6 switching operation/minute local signallingColor indicator hold-in power consumption in VA1.1 VA inrush power in VA11 VA mounting modeClip-on mounting support35 mm symmetrical DIN rail 9 mm pitches2 height81 mm width18 mm depth60 mm product weight70 g colourWhite mechanical durability5000000 cycles connections - terminals2 tunnel type terminal 1.5 mm² for rigid cable(s)2 tunnel type terminal 1.5 mm² for flexible with ferrule cable(s)2 tunnel type terminal 2.5 mm² for rigid cable(s)2 tunnel type terminal 2.5 mm² for flexible cable(s)1 tunnel type terminal 4 mm² for rigid cable(s)1 tunnel type terminal 4 mm² for flexible cable(s) tightening torque1 N.m wire stripping length10 mm product compatibilityNo auxiliary Environment standardsEN 60669-2-1 product certificationsNF noise level10 dB IP degree of protectionIP40 (in modular enclosure) conforming to IEC 60529IP20 conforming to IEC 60529 pollution degree3 tropicalisation2 conforming to IEC 60068-1 relative humidity95 % (55 °C) operating altitude2000 m ambient air temperature for operation-5...55 °C ambient air temperature for storage-40...60 °C Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCAD file (on TraceParts) for A9C15030: iCT plus 20A 1P Uc 230VAC (Version 2.0)iCT+ 20A 1P (Version 1.0)BrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsCertificate CCA FR596479B-M1 iCT 63A according to EN 61095:2009 (Version 1.0)Application solutionsSizeAdd to My DocumentsCatalogue pageSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.