Main range of product9012G pressure sensor typeElectromechanical pressure switch pressure sensor name9012G pressure sensor size1000 psi maximum pressure1000 psi contacts type and composition2(NC-NO), DPDT-DB, Form ZZ, snap action, silver nickel contacts controlled fluidAirNon-corrosive liquidsNon-corrosive gasHydraulic oil (-15...250 °F) fluid connection type0.44 inch 20 UNF-2B conforming to UL 508 pressure switch type of operationDetection of 1 single threshold scale typeFixed local displayWith range scale window Complementary range on decreasing pressure20...1000 psi approx fix differential at mid range59 psi +/- 2.5 % full scale cable entry0.5 inch NPT conduit entrance terminal block type8 screw terminals electrical connectionScrew-clamp terminals, AWG 22...AWG 12 electrical circuit typeControl circuit local signalling1 neon (clear) AC/DC at 120 V (voltage limits:105...125 V [In] rated current6 A (Ue = 120 V AC)0.22 A (Ue = 125 V DC) settingInternal enclosure materialDie cast aluminium alloy 380 pressure actuatorPiston height6.24 in depth4.56 in width5.05 in operating positionAny position materials in contact with fluidTeflonViton fluorocarbon440 stainless steel303 stainless steel short-circuit protection10 A by gL (cartridge) overload and short-circuit protection operating rate<= 120 cyc/mn mechanical durability3000000 cycles repeat accuracy4 % product weight3 lb(US) Environment vibration resistance2 gn conforming to IEC 68-2-6 (f = 40...150 Hz) shock resistance50 gn conforming to IEC 58-2-27 standardsCEUL 508CSA C22.2 No 14 product certificationsCECSA LR25490 class 3211 03UL listed file E12158 CCN NKPZ NEMA degree of protectionNEMA 4/4X/13 conforming to UL 50 ambient air temperature for operation-10...185 °F Offer Sustainability RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
End of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.