View all Nema Pressure Switches
Main range of product9012G pressure sensor typeElectromechanical pressure switch pressure sensor name9012G pressure sensor size425 psi maximum pressure2000 psi contacts type and composition2(NC-NO), DPDT-DB, Form ZZ, snap action, silver nickel contacts controlled fluidHydraulic oil (-40…250 °F)Non-corrosive liquidsAirNon-corrosive gas fluid connection type0.25 inch 18 NPTF conforming to UL 508 pressure switch type of operationDetection of 1 single threshold scale typeFixed local displayWith range scale window Complementary range on decreasing pressure13…425 psi approx fix differential at mid range27 psi +/- 2.5 % full scale cable entry0.5 inch NPT conduit entrance terminal block type8 screw terminals electrical connectionScrew-clamp terminals, AWG 22...AWG 12 electrical circuit typeControl circuit local signallingWithout: [In] rated current6 A 120 V AC0.22 A 125 V DC3 A 240 V AC0.11 A 250 V DC settingInternal enclosure materialDie cast aluminium alloy 380 pressure actuatorDiaphragm nitrile (Buna-N) height5.45 in depth2.63 in width3.5 in operating positionAny position materials in contact with fluidNitrile (Buna-N)Zinc plated steel short-circuit protection10 A cartridge overload and short-circuit protection, type gL maximum operating rate120 cyc/mn mechanical durability5000000 cycles repeat accuracy4 % net weight3 lb(US) Environment vibration resistance2 gn (f= 40…150 Hz) conforming to IEC 68-2-6 shock resistance50 gn conforming to IEC 58-2-27 standardsCSA C22.2 No 14CEUL 508 product certificationsUL listed file E12158 CCN NKPZ and CCN NTHTCECSA LR25490 class 3211 03 NEMA degree of protectionNEMA 4/4X/13 conforming to UL 50 ambient air temperature for operation-10…185 °F Offer Sustainability REACh Regulation EU RoHS DirectiveNot applicable, out of EU RoHS legal scope Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
Product Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.