Main range of product9012G pressure sensor typeElectromechanical pressure switch pressure sensor name9012G pressure sensor size250 psi maximum pressure750 psi contacts type and composition2(NC-NO), DPDT-DB, Form ZZ, snap action, silver nickel contacts controlled fluidSelected corrosive gasesSelected corrosive liquids (-40...250 °F) fluid connection type0.25 inch 18 NPTF conforming to UL 508 pressure switch type of operationRegulation between 2 thresholds scale typeAdjustable differential local displayWithout Complementary range on decreasing pressure5...250 psi approx adjustable differential at mid range15...49 psi +/- 2.5 % full scale cable entry0.5 inch NPT conduit entrance terminal block type8 screw terminals electrical connectionScrew-clamp terminals, AWG 22...AWG 12 electrical circuit typeControl circuit local signallingWithout [In] rated current6 A (Ue = 120 V AC)0.22 A (Ue = 125 V DC)3 A (Ue = 240 V AC)0.11 A (Ue = 250 V DC) settingInternal enclosure materialCast aluminium pressure actuatorDiaphragm (nitrile (Buna-N)) height7.2 in depth5.34 in width7.13 in operating positionAny position materials in contact with fluid316 stainless steelEthylene propylene short-circuit protection10 A by gL (cartridge) overload and short-circuit protection operating rate<= 120 cyc/mn mechanical durability5000000 cycles repeat accuracy4 % product weight18.5 lb(US) Environment vibration resistance2 gn conforming to IEC 68-2-6 (f = 40...150 Hz) shock resistance50 gn conforming to IEC 58-2-27 standardsCEUL 508CSA C22.2 No 14 product certificationsCEUL listed file E12443 CCN NOWTCSA LR26817 class 3218 02 NEMA degree of protectionNEMA 7/9 conforming to UL 698 ambient air temperature for operation-10...185 °F Offer Sustainability RoHS (date code: YYWW) REACh Product environmental profileAvailable
Product Environmental Profile
Product end of life instructionsAvailable Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.