Main relay applicationMotor range of productSepam series 40 device short nameM41 control and monitoring typeLatching/acknowledgement ANSI code: 86Logic discrimination ANSI code: 68 ( option )Switching of groups of settingsAnnunciation ANSI code: 30Circuit breaker/contactor control ANSI code: 94/69Logic equation editor 100 operators metering typePhase current I1, I2, I3 RMS, residual current I0Demand current I1, I2, I3, peak demand current IM1, IM2, IM3Temperature ( option )Voltage U21, U32, U13, V1, V2, V3, residual voltage V0FrequencyPositive sequence voltage Vd/rotation direction-negative sequence voltage ViActive, reactive, apparent power P,Q,S-peak demand power PM, QM, power factorCalculated active and reactive energy (+/- W.h, +/- VAR.h)Active and reactive energy by pulse counting (+/- W.h, +/- VAR.h) ( option ) network and machine diagnosis typeUnbalance ratio/negative sequence current IiDisturbance recordingThermal capacity usedRemaining operating time before overload trippingWaiting time after overload trippingRunning hours counter/operating timeStarting current and timeStart inhibit time, number of starts before inhibitionTripping contextPhase displacement switchgear diagnosis typeTrip circuit supervision ( option )Number of operations, operating time charging time ( option )CT/VT supervision ANSI code: 60FLCumulative breaking current Complementary type of measurementCurrentEnergyFrequencyPeak demand powerPower (P,Q)Power factorTemperatureVoltage protection typeOvervoltage protection ANSI code: 59Directional earth fault ANSI code: 67N/67NCTemperature monitoring (8 or 16 RTDs) ( option ) ANSI code: 38/49TPositive sequence undervoltage ANSI code: 27DDirectional reactive overpower ANSI code: 32Q/40Earth fault/sensitive earth fault ANSI code: 50N/51NEarth fault/sensitive earth fault ANSI code: 50G/51GNegative sequence/unbalance ANSI code: 46Remanent undervoltage ANSI code: 27ROverfrequency ANSI code: 81HUnderfrequency ANSI code: 81LNegative sequence overvoltage ANSI code: 47Directional active overpower ANSI code: 32PBreaker failure ANSI code: 50BFExcessive starting time, locked rotor ANSI code: 48/51LR/14Neutral voltage displacement ANSI code: 59NPhase overcurrent ANSI code: 50/51Phase undercurrent ANSI code: 37Starts per hour ANSI code: 66Thermal overload protection ANSI code: 49RMSUndervoltage protection ANSI code: 27/27S communication port protocolMeasurement readout ( option ) : ModbusRemote control orders ( option ) : ModbusRemote indication and time tagging of events ( option ) : ModbusRemote protection setting ( option ) : ModbusTransfer of disturbance recording data ( option ) : Modbus input output max capacity10 inputs + 8 outputs communication compatibilityModbus RTUIEC 60870-5-103DNP3IEC 61850Modbus TCPIP user machine interface typeAdvancedWithoutRemote Offer Sustainability Product environmental profileAvailable
Product Environmental Profile
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.