Main range of productActi 9 product nameActi 9 PRD1 Master product or component typeSurge arrester with pluggable cartridge device short namePRD1 Master device applicationDistribution poles description1P remote signallingWith signal contacts composition1 SD (1 C/O) surge arrester typeElectrical distribution network earthing systemTN-C Complementary surge arrester class typeType 1 surge arrester technologySpark gap [Ue] rated operational voltage230 V (+/- 10 %) AC 50 Hz [In] nominal discharge currentCommon mode : 25 kA L/PE [Iimp] impulse currentCommon mode : 25 kA L/PE 12.5 A.s [Uc] maximum continuous operating voltageCommon mode : 350 V L/PE [Up] voltage protection level<= 1.5 kV type 2 common mode L/PE [If] follow current50 kA common mode L/PE disconnector device typeAssociated fuse gG 315 A according to standardAssociated circuit breaker Compact NSX100F 100 A curve C - Icu 36 kAAssociated circuit breaker Compact NSX100N 100 A curve C - Icu 50 kA signalling circuit voltage1 A/250 V AC 50/60 Hz mounting modeClip-on mounting supportDIN rail 9 mm pitches4 height90 mm width35.8 mm depth70 mm product weight0.303 kg colourAnthracite grey ( RAL 7016 ) materialPBT (polybutylene terephthalate) response time< 100 ns connections - terminalsTunnel type terminal, downside 2.5...35 mm²Tunnel type terminal, upside 2.5...35 mm² tightening torque4.5 N.m Environment standardsEN 61643-11 : 2012IEC 61643-11 : 2011 product certificationsCE quality labelsKEMA-KEUR IP degree of protectionOn front face : IP40 conforming to IEC 60529Built-in : IP20 conforming to IEC 60529 IK degree of protectionIK05 conforming to IEC 62262 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...80 °C Offer Sustainability RoHS (date code: YYWW) REACh Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.