15370 is replaced by:
Main range of productEasy9 product nameEasy9 CT product or component typeContactor device short nameCT device applicationControl circuit Poles2P [Ie] rated operational current20 A AC-7A pole contact composition2 NO network typeAC control typeRemote control [Uc] control circuit voltage230 V AC 50 Hz Complementary network frequency50 Hz [Ue] rated operational voltage250 V AC 50 Hz maximum power2.5 W 250 V AC [Ui] rated insulation voltage500 V AC 50 Hz [Uimp] rated impulse withstand voltage2.5 kV control signal typeMaintained local signallingMechanical color indicator hold-in power consumption in VA1.2 VA inrush power in VA15 VA mounting modeClip-on mounting support35 mm symmetrical DIN rail 9 mm pitches2 height81 mm width18 mm depth65.5 mm product weight120 g colourGrey mechanical durability1000000 cycles electrical durability100000 cycles at 20 A, 50 Hz, AC-7A conforming to IEC/EN 6109530000 cycles, 50 Hz, AC-5B conforming to EN/IEC 60947-4-1 connections - terminalsPower circuit : 2 tunnel type terminals 2.5 mm² for flexible cable(s)Power circuit : 1 tunnel type terminals 6 mm² for rigid cable(s)Control circuit : 2 tunnel type terminals 2.5 mm² for flexible cable(s)Control circuit : 2 tunnel type terminals 1.5 mm² for rigid cable(s) product compatibilityAuxiliary contactInterference filterMixed control: impulse/latchedTime delay Environment standardsIEC/EN 61095 product certificationsIMQVDEEAC noise level30 dB IP degree of protectionIP40 (in modular enclosure) conforming to IEC 60529IP20 conforming to IEC 60529 pollution degree2 operating altitude2000 m ambient air temperature for operation-5...60 °C ambient air temperature for storage-40...70 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.