08215 is replaced by:
Add to My Products Remove from My Products
- Reason for Substitution: Rebranding
- Substitution date: 31 October 2009
Main rangePrisma product namePrisma G IP degree of protectionIP40 with doorIP30 without doorIP41 with door and canopyIP43 with door, canopy and IP43 gasket product or component typeEnclosure extension enclosure typeFunctional enclosure delivered in kit form device applicationLow voltage electrical distribution enclosure mountingSurface type of front plateWithout (to be ordered separately) product compatibilityFloor-standing enclosure - width 600 mmFloor-standing enclosure - width 300 mmFloor-standing enclosure - width 850 mm number of vertical modules [50 mm]36 number of 18 mm modules per row24 Complementary installation descriptionFloor-standing enclosure - width 600 mm [Ui] rated insulation voltage1000 V on main rear busbars conforming to IEC 61439-2 [In] rated current630 A at 40 °C conforming to IEC 61439-2 [Icw] rated short-time withstand current25 kA (1 s) conforming to IEC 61439-2 [Ipk] rated peak withstand current53 kA conforming to IEC 61439-2 network frequency50/60 Hz enclosure materialEnclosure : treated sheet steel additional informationCan be combined side by side quantity per setSet of 1 height1980 mm, with plinth width600 mm depth205 mm surface finishMattSmooth colourWhite RAL 9001 Environment IK degree of protectionIK07 without door conforming to EN/IEC 62262IK08 with door protective treatmentElectrophoresis treatment and hot-polymerised polyester epoxy powder standardsIEC 62208IEC 61439-2IEC 61439-1 mechanical robustnessSeismic tests : 2.5G conforming to IEC 60068-2-57 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations
Documents and DownloadsLanguage
BrochureSizeAdd to My DocumentsInstruction sheetSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.