08104 is replaced by:
Main rangePrisma product namePrisma G IP degree of protectionIP43 with door, canopy and IP43 gasketIP30 without doorIP40 with doorIP41 with door and canopy product or component typeEnclosure enclosure typeFunctional enclosure delivered in kit form device applicationLow voltage electrical distribution enclosure mountingSurfaceFlush with kit type of front plateWithout to be ordered separately number of vertical modules [50 mm]12 number of 18 mm modules per row24 Complementary installation descriptionWall-mounted enclosure - width 600 mm [Ui] rated insulation voltage1000 V on main rear busbars conforming to IEC 61439-2 [In] rated current630 A at 40 °C conforming to IEC 61439-2 [Icw] rated short-time withstand current25 kA 1 s conforming to IEC 61439-2 [Ipk] rated peak withstand current53 kA conforming to IEC 61439-2 network frequency50/60 Hz enclosure materialEnclosure: treated sheet steel additional informationCan be combined side by side and one on top of another quantity per setSet of 1 height630 mm width600 mm depth205 mm net weight10.78 kg surface finishSmoothMatt colourWhite (RAL 9001) Environment IK degree of protectionIK07 without door conforming to EN/IEC 62262IK08 with door protective treatmentElectrophoresis treatment and hot-polymerised polyester epoxy powder standardsIEC 62208IEC 61439-2IEC 61439-1 mechanical robustnessSeismic tests - 2.5G conforming to IEC 60068-2-57 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectiveNot applicable, out of EU RoHS legal scope Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.