Gas-Insulated Switchgear up to 52 kV
WI is a compact, modular, GIS switchgear for primary distribution. Panels are suitable for configuring single or double busbarswitchgear.
WI is a compact, modular GIS switchgear for Primary Distribution.
- Mainly for applications > 40.5 kV > 185 kV BIL, railway need
- Ratings up to 52 kV, 31.5kA, 2500A, 250 kV BIL
- Uses vacuum circuit breakers
- Circuit connected VT with device to break and isolate VTs HV termination
- Single and double busbar
- Three-phase enclosure
- One or two-phase design
- Space saving
- Intuitive operator guidance
- Easy switching unit replacement
- Environment independent switchgear
ApplicationsWI can be used in power stations, transformer substations, or Railway applications.
EcoStruxure™ for Your BusinessEcoStruxure lets you thrive in today's digital world. Make better business decisions with scalable and converged IT/OT solutions. Learn more
Reach UsHave a question, complaint or is there some feedback you’d like to send us to make your experience with Schneider Electric better? Contact an Expert
Frequently Asked QuestionsEasily find and share the answer you are looking for from our online FAQ service Browse FAQ
Field ServicesOptimize the life cycle of your assets, improve performance, safety, and reduce maintenance costs – all with an experienced provider of complete field services and a partner you can trust. Discover services