The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
|Timer / counters, such as TON, are synchronized between primary and standby. When not primary/standby they are not synchronised. Hence when sync comes back, the value might be overwritten by the Primary or not, depending on the configuration.
Moreover, when the system starts and both CPU are powered up, CPU run first some cycle in WAIT mode before being in Standby mode. If a block (such as TON) is used in WAIT and later on in standby, value have changed because the block is now sync with primary. A bump in the actual value might appear when CPU transits from WAIT to STBY
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!