The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
You can combine XY2CH/CE/CJ E.stop rope pull switch to the XPSAC unit or to the XPSAF5130 unit, like shown in the attached diagram or in the XPSA* instruction sheet.
For the XPSAF5130, it is the standard wiring diagram to use : in the instruction sheet, you replace the E.stop mushroom by the XY2C* rope pull switch to get a PLe category 4 application by using XY2C* model with 2 NC contacts, so XY2CH1xx7x ref or XY2CExxx7x ref. See attached file showing example.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!