The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Can ATV312 drive be programmed to have a 3-contactor bypass?
ALTIVAR 312, ATV312
ATV312 is not available as an enclosed product and there are no programming options for a 3-contactor bypass control. However, the drive relay can be configured for drive running that can pull in a DOC drive output contactor (aux contact) to satisfy a run permissive (assigned to a logic input). The bypass and Isolation contactor are controlled through an external control circuit.
Mostly controlled by the control circuit not the drive. In the EFLEX design w/ bypass, the ATV312 drive would connect the same way as an ATV61. LI2 is assigned to run permissive (nSt) which is satisfied the the DOC contactor.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!