Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
M580 Communication Capability
M580 maximum remote node connectivity
For the M580 PLC, the max number of DIO is based on the CPU and can vary from number of 64 or 128 DIO.
The Max number of Devices is the same as the max number of requests capability. For example with a CPU that supports 128 DIO devices, a User can have 128 DIO devices each with one request or 64 DIO devices each with 2 requests or 32 DIO devices each with 4 requests.
For more DIO devices (aka more communication requests), you can add additional BMENOC03xx modules.
The Maximum number of additional BMENOC03xx network modules is related to the CPU and can vary from 2 to 4.