Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
If an IP address has been saved to flash in a M1E processor then all you have to do is open a project or program you have downloaded into the M1E and edit the configuration off-line. Change the IP address settings in the Extension or Ethernet I/O scanner pages and connect to the controller with the old IP. Download and then save new configuration to flash, go off line and power cycle.
If you do not know the currently saved IP address then you can use the BOOT P LT (boot p light) free software on our web site to assign then new IP. Do not power cycle after assigning new IP from Boot P. Edit the program as described above. Go on-line with the new static IP and download. The newly configured IP will take effect as soon as you log off or power cycle. Go to: eclipse.modicon.com web site and do a search for boot P.