The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
|Modbus TCP server||Modbus TCP slave device|
|Only configure IP address||Need to configure parameters and I/O mapping|
|For Modbus TCP client, all %MW address of server can be R/W.||For I/O scanner, only %IW area (2~40 words) can be R/W, %QW area (2~40 words) are read only, and actual %MW address of slave device cannot be visited.|
|No need to configure “Unit ID”||Unit ID (1~247) should be same the unit ID setting in Modbus TCP I/O scanner.|
|No visualized list for communicated address.||Have a clear and visualized interface to monitor all communicated variables.|
|The connection to one client may be closed when more than 8 connections are needed.||The connection to the Master client is never forcefully closed, when IPMaster Address is configured.|
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!