The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
State of the R1 relay.
Altistart 48, ATS48
All models and serial numbers
Programming or other conditions.
Make sure R1 is assigned as R1F. R1F is the default setting for the R1 relay. If it has been changed to R1I the relay will not change state until a run command is issued to the soft start.
The programming of the R1 relay can be found in menu I/O.
Check and make sure that automat restart feature is not turned on under PRO menu. ATS should be set to no. If unit faults out it will not allow the fault relay to change state anthill the unit has gone through automatic restart phase.
Do a factory reset. Go to DRC and find FCS parameter. Set it to yes and hold enter for 3 seconds.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!