The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
The SFT2826 software was developed originally for displaying waveforms captured on Sepam Series 20, 40, and 80 relays. The software has not had major improvements made since the launch of the Sepam 80 range.
Since the end of development for the SFT2826 software, there have been some changes to the values used for certain parameters in Sepam Series 80 COMTRADE disturbance records. This FAQ gives one example and explains why the user should consider using other software besides SFT2826 to visualize Sepam disturbance records.
Please refer to the IEEE C37.111-1999 standard for more information on the COMTRADE file format. A COMTRADE file from a Sepam relay includes a .CFG file and a .DAT file. This FAQ refers only to the contents of the .CFG file, which can be opened for viewing with Notepad, or any ASCII text editor.
The image below shows the bottom portion of the .CFG file taken from a waveform that was captured on a Sepam 80 relay running firmware version V5.21. As shown, the value of the "nrates" parameter is "01."
The next image below shows a screenshot of the last section of a different .CFG file taken from a Sepam 80 relay running firmware version V8.02. Notice that the "nrates" parameter has a value of "00."
The SFT2826 software was not designed to open COMTRADE files having the "nrates" parameter set to "00." Therefore, the software cannot be used to open such files, and an error message will be encountered if this is attempted. This modification in the Sepam 80 COMTRADE files was made starting in the V8.01 firmware version (approximately). The purpose of this modification was to handle variable sampling rates inside a single disturbance record.
To resolve this issue, it is recommended to use other software applications such as WaveWin or Transview (by OMICRON) to open Sepam COMTRADE files. Both of these applications are able to open all Sepam waveform files, regardless of the firmware version of the relay used to capture the waveform. Although SFT2826 could still be used to visualize waveforms captured using older firmware versions, it is recommeded to use WaveWin or Transview to view all Sepam waveforms in general.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!