Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The VIP 400 (and 410) self-powered relays use custom sensors that are designed specifically for this relay. As such, the CUa / CUb / CUc sensors cannot be ordered as loose components, and some details such as the IP rating are not given in the VIP400 user manual. This FAQ contains some details that relate to the IP rating of the VIP400 sensors.
a) the sensors are type tested according to the IEC60044-1 and IEC61869-2 standards. The sensors are not subjected to the "routine tests" defined in those standards.
b) the sensors are enclosed in a moulded casing with wires that extend out from the casing, so they are theoretically hermetically sealed. However, they have not been designed for outdoor applications, and this type of usage is not approved by Schneider.
c) from the design perspective, the IP rating for the CUa and CUb sensors is IP67 with the terminals not submerged, and the conductor of the wires exposed.
As a general remark, each installation of the VIP400 relay must be validated separately, which includes the switchgear that houses the VIP400 relay. Therefore, the IP rating of the sensor cannot be considered in isolation - the complete cubicle must be designed and validated separately for each project. This information was provided by the Schneider Instrument Transformer experts in France and Italy.
Sign up for all the latest solutions, offers and best practices straight to your inbox.