Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
This article discusses how to control an ION module and in turn an ION meter. This includes resetting, triggering and changing state of a module registers.
Applies to all ION meters (7330, 7650RTU, 8600, ...).
Modbus Tester or any other Modbus program or device with write capability.
Refer to Modbus Map for ION Meters document that lists each module (ION register) and its corresponding Modbus register based on the ION module number.
Controlling an ION meter by sending commands using Modbus protocol. The commands can be written to the following modules:
For demonstration purposes, a value will be written to External Numeric 1 and 4 modules. Writing to External Boolean and External Pulse modules follow the same procedure.
1. Determine Modbus addresses by referring to Modbus Map for ION Meters document
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!