Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A user wants to have a log of voltage and current angles for each phase in an ION meter.
ION Setup V3.0
A log that contains the Voltage and Current phase angles is not configured by default.
This example will use an ION8600.
1) Using ION Setup, a new data recorder will need to be made. This can be done by first selecting setup screens from View -> Setup Screens. Then, hold the control button on your keyboard and left click on your meter device. This will enable advanced mode on your meter and display a list of modules. Select the "Data Rec Modules". Right click in the empty space on the right of the screen and insert a new module.
2) Double click on that new module to open it. You will see a password prompt and a warning. The default password for the meter is 0. Read the warning and press OK.
3) The next step is to create a new periodic timer module.
4) Double click on that new module to open it. Set it to a time period of your choosing such as 900 seconds. This will trigger your data to record every 900 seconds for example.
5) In your data Recorder that you made, one of the Inputs will be "Record" and here you will select the timer you just made.
6) Then for Source's 1 through 6, select your Harmonics Module, then V1 Harmonics, then V1 Phasor Angle. Repeat that for V2, V3 and I1, I2, and I3.
7) The Knowledge Base (KB) article FA211845 (How to Create a Data Log View for a Custom Data Recorder using ION Setup) explains the steps to get your data recorder to function.
You should be able to find out what feature set your ION8600 meter (which was used in this example) has by looking at the Device Properties of your device in ION Setup and looking at the Display tab. This will assist you when using the linked KB article for choosing the right file folder.
8) With that done, your data recorder should be viewable on the Data Screens view under the folder "Data Recorders".
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!