The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
To support full communication & robust exchanges on BMX/BME CRA corrections had to be done on CRA.
Facts and Changes
This creates incompatibility with Input_char_QX and Print_char_Qx in Unity Pro V7 EFs due to communication checks in CRP.
The EFs have been modified in Unity Pro V8 to support new BMXCRA firmware version.
In case a customer is using a Unity Pro V7 application, including "Input_char_QX" and "Print_char_Qx"(with NOM for example) and he adds a new BMXCRA31210 (after the launch of the M580) with the lastest firmware, the application will not work.
Causes and Fixes
The customer will have to:
- either, update the application to Unity V8
- or, downgrade the firmware of the BMXCRA31210 ( SV 1.30 ) to previous version.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!