Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A user may need to know the maximum pulse frequency that the on-board digital input of a PM800 can receive?
C1 and S1 (ports 6 and 7) on the PM800 series meter.
While wiring mechanical meters or other solid state devices which are capable of sending digital pulses to indicate a change of their states, one might be interested to know, what is the maximum frequency of the incoming pulse train the PM800 is capable of accepting.
For the on-board digital input ports of the PM800 series meters, the maximum frequency of the incoming pulse train is 25 Hz.
The minimum pulse width was, found at 25 Hz, to have a duty cycle of approximately 10% (4 ms) (all tests were done at 24 V).
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!