Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
To connect to a Magelis XBTN200/400 with a Magelis Logo you need the following:
TSXCUSB485 (USB to RS485 adapter. Rotary switch set to 0 TER Multi. Polarization On.)
XBTZN999 (RJ45 to RJ45)*
XBTZ925(A) (1 side connected to XBTXN999 side, 2 connected to Magelis side.
You can also make your own cable (This pinout only works with XBTN200/400 with Magelis logo)
RJ45 Male (TSXCUSB485 side) to RJ45 Male (Magelis Side)
5 to 4
4 to 5
7 to 7
8 to 8
8 and 1 jumped on Magelis side
6 and 8 jumped on TSXCUSB485
*XBTZN999 is not required for the XBTN200/400 with the Telemecanique logo.