Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
ENM setup page opens properly when it is opened directly in a browser, However, when it is being opened from PowerLogic Scada, the following error occurs:
In this case the problem was due to downgrading Internet Explorer. It applies to Citect and Browser Emulation setting.
PowerLogic Scada 7.3
IE8 with compatibility mode enabled.
The FEATURE_BROWSER_EMULATION feature defines the default emulation mode for Internet Explorer, below are some of the supported values:
9999: Windows Internet Explorer 9. Webpages are displayed in IE9 Standards mode, regardless of the !DOCTYPE directive.
9000: Internet Explorer 9. Webpages containing standards-based !DOCTYPE directives are displayed in IE9 mode. Default value for Internet Explorer 9.
8888: Webpages are displayed in IE8 Standards mode, regardless of the !DOCTYPE directive.
8000: Webpages containing standards-based !DOCTYPE directives are displayed in IE8 mode. Default value for Internet Explorer 8
7000: Webpages containing standards-based !DOCTYPE directives are displayed in IE7 Standards mode. Default value for applications hosting the WebBrowser Control.
Complete information regarding browser emulation can be found in the link below:
In registry find the Citect32.exe key under:
Citect32.exe = (DWORD) 00009000
It could have a value of 9000 or 9999; change it to 7000. Restart PowerLogic Scada and observe the problem is resolved.
Values of 8000 and 8888 which are for IE8 did not work.