Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Ensure that the ethernet network, IP addresses and subnet masks are configured properly and all devices can be pinged. Now verify that in the M1E IO scanner setup that the 'Read Ref Slave' memory location is set for 45392 and not 40001 as would be the case if scanning a Momentum IO base with an ENT communication adapter. This is a common error with Advantys STB.