Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Advantys STB Actuator Power warning message
No. A warning flag will not prevent you from building a project. This flag is calculated based on the worst case scenario for what the modules can handle. A more accurate calculation would be to take into account the actual current draw of the field devices being used. If there is no configuration software, then the calculation would have to be done manually. Adding another PDT will increase actuator or sensor power. Also if the current draw is actually above the allowable limit, the PDT fuse(s) will be blown.