Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The product selector will not allow selection of MOD C07.
Enclosed 22 Soft Start
Enclosed 22 Soft Starts with Power Circuit B05 or S05
Attempting to combine Power Circuits B05 or S05 with Pilot Light Cluster C07.
Shunt Trip Power Circuits B05 ( Basic Shunt Trip ) and S05 ( Full-featured Shunt trip ) are not compatible with Pilot Cluster C07. The Fault indicator pilot on C07 is controlled by the ATS22 trip status relay output. When a shunt trip power circuit is used, the ATS22 trip status relay controls the shunt trip and therefore is not available for pilot light control. In a fault condition, the shunt trip will interrupt power at the main disconnect and all indicator lights will be out.