Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The product selector will not allow selection of MOD C07.
Enclosed 22 Soft Start
Enclosed 22 Soft Starts with Power Circuit B05 or S05
Attempting to combine Power Circuits B05 or S05 with Pilot Light Cluster C07.
Shunt Trip Power Circuits B05 ( Basic Shunt Trip ) and S05 ( Full-featured Shunt trip ) are not compatible with Pilot Cluster C07. The Fault indicator pilot on C07 is controlled by the ATS22 trip status relay output. When a shunt trip power circuit is used, the ATS22 trip status relay controls the shunt trip and therefore is not available for pilot light control. In a fault condition, the shunt trip will interrupt power at the main disconnect and all indicator lights will be out.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!